Envirosafe’s 500 gallon small fleet fuel system is the perfect bulk fuel storage solution for small commercial fleets, golf courses, small farms, and other small diesel and unleaded gas dispensing applications for commercial use.
The Small Fleet systems come equipped with ¾ hp Tuthill transfer pump, either FR 711 or FR 319 depending on the fuel type, and flow rate required. If the pump is mounted on a bracket below the top of the tank, the piping will include a required ball valve and anti-siphon valve to prevent spill in the event of an accident and pump maintenance. All of our systems come with automatic shutoff nozzles, swivel, and breakaway for ease of use and extra safety measures.
The Small Fleet systems come with a 7 ½ gallon overspill bucket for filling operations. The Small Fleet system comes standard with 818 clock gauge to measure the tank levels. There are standard upgrades available, 918 clock gauge with the high-level alarm set to sound at 90% capacity when filling the tank and overfill prevention valve set to shut-off at 95% capacity to prevent overfilling the tank. Please consult with your local authorities to find out if either one or both upgrades are a requirement in your area.
Because our systems are double walled, they come with a mechanical interstitial monitoring gauge as a standard feature. There are upgrades available to use electronic interstitial monitoring system. We offer a few options for fuel and fleet management to monitor and track fuel levels, fuel consumption, and delivery. Please ask your sales representative about optional upgrades available to make tank monitoring and management more convenient to save you time and money. Thank you for your interest in Envirosafe Above Ground Fuel Systems. We sincerely appreciate your time and interest in our products.
500 Gallon Small Fuel Fleet System Features
(1) UL-142 Flameshield or UL-2085 Fireguard Tank Mounted on Saddles
(2) 4” 8 Oz Emergency Vent Male w/O-ring
(1) 2” Stack Vent (12′ above grade)
(1) 7.5 Gal Overspill with Lockable Cap. EQ #726
(1) 818 Clock Gauge w/ Standard Float
(1) Engineered Hurricane Tie Down
(1) Interstitial Leak Gauge
(1) Tank Decal Kit
(1) Envirolastic 940 DTM Polyaspartic Urethane for High Performance Finish
(1) Fill-Rite 319VB Hi-Vol 1” Assembly Digital Meter, 1” Auto Nozzle & 18′ x 1” Hose
(1) Overfill Valve
(1) Husky 1” Breakaway & Husky 1” Swivel
(1) Cim-Tek 1.5” Filter Adapter & 1″ Inlet/Outlet
(1) Bracket, Piping, Ball Valve & Anti-Syphon Valve
(1) 18” Man way for easy inner tank accessibility
(1) UL Labeled & Listed (Per your local Fire Marshall)
(1) Step ladder with Platform
(6) Replacement Fuel Filters
STEEL THICKNESS 3/16” SHELL & 1/4” HEAD
(1) Touch-up paint
* Unleaded System will come with a Vapor Lock Relief Valve
UL 2080 Listed “Fire Resistant”
UL 2085 Listed “Protected”
Both Inner & Outer Steel Tanks built to UL Standards
Uniform Fire Code UFC “Protected” Tank
National Fire Protection (NFPA) 30 & 30A
International Fire Code (IFC)
California Air Resources Board (CARB) for Air Emissions
Steel Tank Institute (STI) Standard F941 for Thermally Insulated Aboveground Storage Tanks
Tested Two-Hour Fire Resistance
Built to UL 142 Standards
Tested by Southwest Research Institute to SwRI 97-04
Double-Wall Tanks Have Fully Monitorable Interstitial Space for Leak detection
500 Gallon Small Fuel Fleet System Maintenance
The tank operator should preform periodic walk-around inspections to identify and repair areas of damage to the vessel or the coating itself and check for proper drainage around the tank area. It is imperative that the tank exterior be inspected periodically to ensure that the integrity of the coating is maintained. The frequency of periodic repainting will be based upon environmental factors in the geographic area where the tank is located. Special consideration should be given to the selected of the paint, surface preparation and coating application. The coating selected should be suitable for use with the current coating, or the existing coating should ne removed. The coating selected should be of industrial quality Proper site preparation and maintenance are vital to ensure drainage of surface water. Should ground conditions change or settlement occur, take the appropriate steps to maintain proper drainage and prevent standing water near or under the tank area. For diked tanks, remove any product spills immediately. Be sure to dispose of hazardous material properly. For diked tanks fitted with a drain, drain off water only. Drain openings are required to be maintained liquid tight. The primary tank shall be inspected monthly for the presence of water at the lowest possible points inside the primary tank. Remove any water found. Water and sediment in fuel can cause plugging of filters. Also, bacterial growth, originating form the fuel can cause corrosion of tanks and lines. For procedures on how to check for the presence of water and removal of water, refer to the STI R111, Storage Tank Maintenance/For copies of the RP and more information, please go to www.steeltank.com. Failure to adhere with these maintenance instructions may void your warranty.
Tank relocation requirements – often aboveground storage tanks are relocated. The following instructions are to be followed when this occurs: All steps are to be documented and the documentation is to be kept for the life of the tank. The hazards associated with the cleaning, entry, inspection, testing, maintenance or other aspects of AST’s are significant. Safety considerations and controls should be established prior to undertaking physical activities associated with ASTs . Cleaning of tanks must be per state and local jurisdiction requirements. Refer to the STI Standard SP001, “Standard for the Inspection of Aboveground Storage Tanks” for requirements concerning tank inspections. The SP001 Standard details requirements for inspections based on the tank installation and age. A tank must undergo the appropriate insurance prior to relocation. In addition, the tank must be subjected to a pressure (or vacuum) test.
500 Gallon Small Fuel Fleet System Accessories
- Epoxy Lining
- Polishing System
- Level Monitoring
- Fuel Management